About Data Center
Data centers of the RENTER project
RENTER project uses for its work two geographically distributed data centers united by the reserved optic network:
DPC «NORD» (DataLine) (Company "Dataline, Moscow, Korovinskoe Shosse. 41)
DPC «Agava-Sever» (Dolgoprudny, Zhukovskogo Str., 3)
Stability and quality of communication provided by duplication of external channels.
At the moment, to the data center RENTER are connected TV operators such as:
- — Beeline ("VimpelCom")
- — RETN (JSC "RetnNet")
- — Di-Net (ZAO "Digital Network")
- — traffic exchange point DataIX
All connections are made via optical modules 10Gb / s.
Each uplink has excellent connectivity with MSK-IX
MSK-IX («Moscow Internet eXchange») is the largest in Russia point of the Internet traffic exchange (IX), located in Moscow. Included in the top five in the world IX.
MSK-IX is included in the 5 largest traffic exchange points in the world in the number of connected operators and in terms of traffic.
The list of participants and statistics MSK-IX published on the official website. On March 3, 2013 373 participants were connected to MSK-IX, the total peak of traffic through a network of MSK-IX overcome a mark of 1 Tbit / s.
Official site MSK-IX http://www.msk-ix.ru/
24/7 monitoring of highly qualified system administratorswww.dtln.ru
Clock video surveillance in all areas and server rooms
The system is built on the cooling equipment of Hiref. Precision dual-circuit freon air conditioning TADR1002 with the downflow air is installed in the computer hall.
The cooled air from the air conditioner is supplied under a raised floor and then through the perforated floor tiles, blown into the "cold" corridors between the racks.
Air conditioning in the halls is reserving on according to the scheme N + 1 (one air conditioner in the room - a reserve). External condensing units (two for each air conditioner) are placed at the site next to the building.
Electricity from the city served by two cable entries on the two step-down transformer.Uninterruptible Power Supply - APC-MGE Galaxy 7000.
UPS battery capacity is designed to operate client racks and data center information infrastructure for 6 minutes (time, enough to start the diesel engine with a large reserve).
Uninterruptible power supply is provided by a diesel generator set (DGS) in container type, working on the busbar that provides DGS a level of redundancy 3 + 1.
Oil and antifreeze in the diesel engines are constantly in a heated state, thereby generating set constantly ready to launch (start-up of the engine takes less than a minute).www.dtln.ru
Automatic gas fire extinguishing system
Data center is protected with automatic gas fire extinguishing system designed for early detection of a fire, the alarm and automatic fire extinguishing. As an extinguishing agent used Freon 125, which is stored in the fire-extinguishing modules.
A method of extinguishing - the volume by filling the protected space by vapor of refrigerant 125 to create a fire extinguishing concentration.Smoke detectors are placed in the working space of the hall and under the raised floor for detecting a fire in protected premises.